UV Sterilizer : Ultraviolet Disinfection of Drinking Water
I produced Drinking Water UV Sterilizer (hereinafter referred to as ultraviolet disinfection) working principle is to use a wavelength of 225nm-275nm UV role in the killing of microorganisms for the water to be purified. When water flows through the disinfection by ultraviolet light, water, bacteria is killed.
First, the product features:
1, ultraviolet disinfection sterilization speed, the effect does not change the water physical and chemical properties do not increase the water taste and odor, no carcinogenic chloroform, once installed, easy to operate, easy management.
2, UV sterilizer cylinder using high-quality food grade stainless steel plate processing, service life is 5-10 times that of aluminum products, high pressure, metal ion contamination.
3, UV Germicidal Lamp selection of the identified state health departments, epidemic prevention departments of professional products, low-voltage 30w, main lines 235.7nm, the highest rate of this wavelength ultraviolet disinfection, more than 98%, and low power consumption, continuous service life of up to 3,000 hour or more.
4, and electrical control box with one design, appearance, save space.
Second, the scope:
Applicable to rivers, Wu Tong and well water of small water systems, especially with high water tank and storage tank with a water supply system. Installation of ultraviolet disinfection in the high water tank and storage tank at the exit can effectively solve the secondary pollution caused by harmful bacteria exceeded due to the problems, but also for food, beverage, brewery industries and the swimming pool water disinfection.
Third, installation, commissioning:
1, ultraviolet disinfection should be installed horizontally (prohibited vertical installation).
2, UV sterilizer cylinder shall withstand the external pressure.
3, UV sterilizer should be installed at the outlet of the tank or water tower, Flow volume, high pressure or excessive network while installed on the user's trunk closer (branch) is better.
4, extending from both ends of the UV sterilizer outward, should be left ≥1 ≥0.4 m m space, in order to replace the lamp, UV sterilizer should remain 0.6 meters barrier-free space between the front control panel for easy maintenance .
5, regardless of choice of one or more UV sterilizer in parallel, shall install a bypass pipe and valve to facilitate maintenance.
6, reasonable choice installation location, pay attention to the electronic control part of the water and moisture.
7, according to the nameplate voltage, the power to select electrical outlet, wire or connector strips.
8, quartz glass tube and the UV lamp is a valuable fragile items, transportation, installation, use should be avoided bump.